AUDIT ENERGI PADA GEDUNG PERKULIAHAN FT F1 DAN GEDUNG PRAKTIKUM DAN PERKULIAHAN FKIK F2 UNIVERSITAS MUHAMMADIYAH YOGYAKARTA
SYAATNUARTORO, MUHAMMAD BAGAS
MetadataShow full item record
The energy audit in buildings is carried out to determine the load profile of electricity use and avoid waste of energy which will make the payment will be even greater. With the audit, it is expected that the building will be efficient so that it saves payment costs. The object of this research is the lecture building of the Faculty of Engineering building F1 and the building for tutorial and lab skills at the Faculty of Medicine and Health Sciences. , The area of each room, and the time of use which will be used to determine the Energy Consumption of the building and then look for Energy Consumption Intensity in accordance with SNI-03-6196-2000 and at the end can find the Opportunity to Save Energy and costs. The formula for IKE is the division between energy consumption and the building area. The results of this study are kWh The total energy consumption of the F1 building lectures at the Faculty of Engineering is 5967.71 kWh and with a total area of 1180.2 m2 then the energy consumption intensity is from the calculation so IKE is 5.05 kWh / m2 / month with the category of Very Efficient. The total amount of energy consumption from the Lab Skill and Tutorial Room building of the Faculty of Medicine and Health Sciences F2 is 5086.86 kWh and with a total area of 1155.36 m2 the energy consumption intensity is from the calculation so IKE is 4.402 kWh / m2 / month with Very Efficient category. PHE in F1 is 912.8 kWh / Month with a savings percentage of 17.66% and F2 PHE is 902.03 kWh / Month with a savings percentage of 17.74%.